Error A006 means that the heating source defaults to elements due to compressor malfunction. The following steps can help you check the issue.
- Confirm fan is operational while the compressor is on. (In case the fan is not operational, check continuity from the middle (ground) terminal to either outside terminal. If there is a 60V or higher reading, the fan should be running and will need to be replaced. If not, replace the control board (rare)).
- Make sure the filter screen is clean.
- Inspect compressor and surrounding components for any obvious signs of the refrigerant leak (oily residue) If the compressor is not operational or there are signs of leakage, the unit will need to be replaced as we do not service sealed system parts.
Zwell is dedicated to getting homes closer to net zero through the installation of new energy-efficient hybrid water heaters. We are not currently equipped to do service or repair visits but we want to be as helpful as possible. Feel free to reach out to us here or for more information, you can contact the Rheem Hybrid Technical Services Department at 800-995-0982.